Part 1. WiFi Configuration&Monitor System
Please refer document ‘Monitor system setup for Distributors’or ‘Monitor system setup for endusers’to set the password. Users can download this document in the download section
When wifi dongle works normal, three LEDs should be solid on. If the middle LED in the wifi dongle is flashing or you can not find your inverter in the monitor system, this may caused by the following reasons,
(1) Wifi password is not set or wrong. If you have not set wifi password, please refer the ‘‘Monitor system setup for Distributors’or ‘Monitor system setup for endusers’to set the password.
(2) If you have already set the password, please connect your mobile or PC to wifi donlge hotspot, and visit website 10.10.10.1 . Both username and password are ‘Admin’, after login, please check if the wifi dongle can get IP address, if can not, it means wrong password, if yes, it means the password is right.
(3) The wifi has some problem, after login and find the wifi module has already get the IP address, if the connect status for ‘Network 1 state’ is still disconnect, it means the wifi has some problem. Please check your wifi and internet.
(4) If you have get the IP address and your TCP Clinet State is Connected, Please check if you have already add this datalog SN to your station. When you register in the APP for the end-user account, you need to input the SN of wifi module, then the datalog is added to your station automatically. If you use a distributor account and installer account, please login the web and go to ‘configuration’->’station ‘ to add station first, then go to ‘datalog ‘ page to add the datalog. Then restart the wifi dongle.
Local connection is available in the Luxpower APP, please check the ‘Monitor system setup for endusers’ file, which is available in the download section
Please contact local distributors or firstname.lastname@example.org and tell them the inverter and wifi dongle SN, we will help you to find username and reset the password.
If your models are standard model, you just need to add all datalogs to your station as below.
If you have parallel model for your installation, set them to paralleling group, so that you can see all inverters easily. Please go to Overview->Device Overview->choose the station ->click Parallel->Input Parallel index(you can put 1,2,3)->Save
Please refer Monitor system setup for Distributors’or ‘Monitor system setup for endusers’to set the wifi password again.
Please contact local distributors for firmware update, and it is free.
Please check network strength ,also this could be caused by losing connection of WiFi module with returning ‘Device offline’
CT is no reading. Please make sure that the CT is connected in the right place.
Part 2.Battery Connection & Operation
(1) If work with the lithium battery , please make sure it is compatible with the Lux units(please check with your installer or distributor)
(2) If the battery is compatible with Lux unit, please choose the battery type or brand on the LCD(Setting->Set battery->Choose Li battery->Choose battery brand)
(3) The cable inside the Luxpower carton box is used to Pylontech battery, if you are using Pylontech battery, you can use the cable directly. Please note there is lable attached with the cable, do not plug the battery side to the inverter side. If you install more than 8pcs Pylontech battery, you need a hub for the battery.
(4) Make sure you have use the right communicate cable between battery and inverter(Different battery has different communication cable) . The terminal for battery communication port definition is as below:
(5) Please remember to connect Master battery to inverter if you have a battery group, and set Master battery for the battery group.(Please contact battery manufacture for battery group setup)
You can set the battery by LCD or website(distributors), please refer user manual to set battery and choose battery brand
The inverter will report battery failure if the battery can not be charged or discharged, please contact your battery supplier to check the problem.
1、Check if the battery connection is reversed.
2、It is suggested to use multimeter to measure the battery voltage before connect to the inverter (input voltage range 40-60V), please pay attention to the battery polarities.
3、After you check battery output voltage is normal, please check the breaker between inverter and battery is closed.
If you are using lithium battery , please make sure there is no communication error between inverter and battery .
if you are using the lead-acid battery ,please check battery setting and change it to lead-acid mode .
There are three stages for lead acid battery charge . For charge part, please set CV voltage and floating voltage.
For discharge part, please set the discharge cut off voltage for on grid and off grid.
(1) Discharge cut-off level and discharge hours setting .
Grid available : Battery will discharge when 100% ≥ SOC ＞ On-grid discharge cut-off level(or BMS limitation)
Grid unavailable : Battery will discharge when 100% ≥ SOC ＞ off-grid discharge cut-off level(or BMS limitation)
(2) The system will not discharge if you enable AC charge at setting time
Back-up function should be enabled on APP or web page. And also check if it is set to ‘standby’ in the monitor system before enable EPS function.
When the inverter works in charge mode with lead-acid battery and the breaker of battery is forgotten to be turned on, and the charge power is almost zero, then the inverter will think it is fully charged and adjust the soc to 100%. When the inverter works in discharge mode and the breaker of battery is forgotten to be turned on, and there is no enough energy to discharge and battery voltage will drop rapidly, then the inverter will think the battery energy is ran out and adjust the SOC to 0% . Please restart the inverter to reset the SOC.
For the old firmware(Before 2020/12), there are two stages for Lead acid charging. After the battery is full charged(charge to the setting voltage shortly), the system will not charge the battery until the battery voltage is lower than 50V or discharging power has happened.
For new firmware, there will be three stages, and users can set CV charge voltage and floating charge voltage. And it will charge the battery to 100%
If you have any problem when using lead acid battery with old firmware, please contact Luxpower for firmware update
The SOC calculation of the lead-acid battery is not accurate. It’s difficult to draw a exact Volt-soc curve because the voltage changes a lot when charging or discharging happens. So for lead acid battery, please focus on the voltage level.
The charge/discharge power will limited by both by inverter and BMS. For example , the discharge power limitation for inverter is 3000W, and there are only two Pylon US2000 connected to the inverter, so the peak discharge current limited by BMS is 25A*2=50A, so they system maximum discharge power is about 50V*50A=2500W.
There is a fuse between the battery side and the inverter, and the fuse failure causes the battery to be open.
This is a system problem. LLC is out of order and the battery side short circuit. Please contact the local distributor and send back the inverter for inspection and repair.
1. Please check whether the battery wiring is correct.
2. Please contact the local distributor to check whether there is something wrong with the battery BMS.
Part 3. About Lux unit Operation
‘Back-up’function can be reset only when the inverter is in standby status, so you can set‘Standby’ first and then enable /disable ‘Back-up’function and set it to ‘Normal’.
The suddenly change of load consumption will cause the energy to be fed to or imported from the grid at one moment, and battery begins to compensate the loads with match power in 1-2 seconds after having detected the change. The inverter detects the load change thru the external CT and there is a 500 milliseconds delay to respond.
For examples, the balanced load consumption is 300W, and battery discharge 300W to compensate the loads , but if suddenly the load comsumption changes to 170W ,the excessive energy(300-170=130W)will feed into the grid at one moment .Instead , if the balanced load consumption is 170W and suddenly changes to 300W, then the excessive energy (170-300=-130W) will taken from the grid at one moment, and battery will adjust the compensation to reach another balance.
These work modes are for PV energy management. Lux unit will work in self-use mode as default
- Self-use mode : the priority of PV energy management is like this: Compensate the load consumption > Charge the battery > Feed into grid.
- Charge priority mode : If you don’t want battery to discharge during the daytime, you can enable ‘charge priority’ within the charge hours with given power limitation.And the priority of PV energy management is like this: Charge the battery > Compensate the load consumption > Feed into grid.
- Charge last mode : If you connect a low capacity battery to a high PV producton system and excessive power can be sold to the grid with a good price, you can just charge battery till the PV production is higher than the set value. And the priority of PV energy management is like this: Compensate the load consumption > Feed into grid > Charge the battery .
Yes, Luxpower inverter support pure off grid running for islands and the standard warranty time is 5 years
Yes, Luxpower inverter can work with three phase meter and will get power for the other two phases and give compensate to the other two phases.
Phase A Load :500w Phase B Load:600w Phase C Load:700w
then inverter will output 500+600+700=1800w in phase A.
In some countries, the export power of phase A will compensate the cost of phase B and phase C, so please contact the power company before install a three phase meter.
You can enable charge priority in the monitor system and then the solar will used to charge battery first, the battery will not discharge until load shedding, this function is usable for the area where always has load shedding.
This is the problem of abnormal sampling circuit. There are large deviations in the BUS sampling, AC voltage sampling and the actual situation of the inverter. Pleasr contact the local distributor to replace it and it is free.
It is so the PV2 terminal contact is bad that results in abnormal sampling.Pleasr contact the local distributor to replace it and it is free.
From the monitoring data, it can be seen that the CT has not been installed normally since the very beginning of the power station, so we can't see where the CT is installed.Please confirm the localation
This is a system problem. Please contact the local distributor to upgrade the program and restart the inverter, and it is free.
The reason why the inverter triggered Voltage BUS high is because of frequent off-grid switching, which increases the probability of high BUS Voltage in the grid-connection switching process. Please contact the local to upgrade program and shield island detection.
The LLC abnormality caused the LLC capacitor to bulge and the MOS tube to explode. Please contact the local distributor to replace a new one.
The spring key is in bad contact with the panel. Please contact the local distributor and send it back for repair.
It's because the leakage current too high. Please check the grounding wire and contact the local distributor.
The reason to exit is "there is an on-grid connection fault or AC is abnormal but the off-grid condition is not satisfied, so exit to Standby". Please contact the local distributor to check.
There is something wrong with the SPS transformer. Please contact the local distributor to change.
It is so abnormal city electricity leading to on-grid and off-grid repeatedly switching that caused flicker. Please contact the local distributor to change the settings and upgrade the program.
Rsvd is short for reserved. Also, it is generally considered to be a simple reservations and capacity management software platform. Rsvd means a reserved bit in the register as shown at 04_SONAR-5K-WPV-Guidance.pdf
Part 4. Generator Connection
Yes, all lux units support generator function
You can connect the generator output to inverter Grid terminal. If you have both grid and genset input, you need an external ATS
You should enable ‘Micro-grid’ function via the APP or Web page while you connect the generator to the Lux unit. Battery will get charged when the generator is turned on.
Yes, A external control box (please check with your installer or distributor if you need it ) is needed , and your generator should support external control function.
The generator will be automatically started when battery voltage is lower than the cut-off value or there is charge request or stop charge flag is set
Part 5. Parallel System Connection
(1) Check CAN cable connection is connected to the right COM port
(2) Check parallel setting for master/Slave part, there should be one master in the system, all the others should be slave, you can set master or slave by the LCD or website.
(3) Check if the balance resistor is on in the begin and end of the communication loop
(4) If it is a single-phase system, please check if you have paralleled all “Grid”ports at the same phase , and “L”line and “N”line of each port mustn’t be reversed and check if“single phase master”has been selected. If it is a three-phase system, each phase should have at least one Lux unit ,and check if “three -phase master” has been selected.
(5) If all details above are correct ,and there is still showing “E015” , try to set “Clear Detected Phases” to each Lux unit.
Please refer to ‘Parallel connection guidance’ to connect the parallel communication cable
(1) CAN cable connection is connected to the right COM port
(2) If you have make the parallel communication cable yourself, please make sure you have make the right cable, otherwise, it will interrupt the wifi communication